8 Perfect Rittal Thermostat Wiring Diagram Images
Related images in this posts:
Other recommended photo ideas:
Rittal Thermostat Wiring Diagram - 9 four.4 connecting the condensate discharge a bendy condensate discharge hose ø 2 mm ( / 2 ) may be suited for the air/water heat exchanger (see fig. Four). The condensate discharge ought to be laid with a suitable and consistent gradient (no siphoning). Should be laid without kinks. Should now not have a discounted cross-section if prolonged. The condensate hose is available as an accessory (refer additionally to add-ons within the rittal catalogue). 4 meeting and connection fig. 5: connecting the cooling water inlet and return key cooling water connection (inlet) 2 cooling water connection (go back) three condensate discharge fig. Four: three connecting the condensate discharge key cooling water connection (inlet) 2 cooling water connection (go back) three condensate discharge connect a appropriate hose to the condensate nozzle (at the bottom of the unit) and relaxed it with a hose clip (with 2 nm torque). Lay the condensate hose, e.G. Right into a drain. To save you the water from backing up, the hose move-section should now not be constrained! B) constant pipework with g three / 8 external thread (included with the deliver) in its brought nation, constant pipework with a g three / 8 external thread can be linked to the air/water warmth exchanger for both the inlet and the return. To this give up, you'll want to do away with the connector sleeve connected to the tool (see fig. 6). The fixed pipework should be tightened with 25 nm. 4.5 connecting the water connection there are 4 exceptional options for connecting water to the air/water warmness exchanger. A) / 2 connector sleeve (covered with the supply) in its delivered state, a compression-proof, bendy cooling water hose ø 2 mm ( / 2 ) can be linked to the air/water warmth exchanger for each the inlet and the go back. The cooling water hose must be laid with out kinks have to now not have a reduced cross-section if extended and, if essential, must be insulated. Fig. 6: 25 nm dispose of the connector sleeve notice: whilst loosening the connector sleeve, it's miles crucial to make certain that the precise on the tool give up is fixed with an sw22 open-jawed spanner. The connection in the device should develop a leak. Rittal air/water heat exchanger meeting commands 9.